This home is located in Twain Harte, California and had an existing heat source but no solution for cooling. The couple living in the home had just retired and wanted to enjoy their home more now that they would both be in the home for longer periods of time during the day.
Problem: No cooling source, and no place to run ductwork. The customer also wanted to have a more contemporary look to the wall mounted units.
Solution: We installed two designer series wall mounts in the home. A larger one for the living space and a smaller one for the bedroom.
This home had the challenge of getting the living room units refrigerant lines to the back side of the home as there was only a crawl space through part of downstairs and a finished second bedroom. So we had to run the refrigerant lines horizontal in the front of the home, wrap around back side of the gutter and come down the wall to allow the drain to have fall. From there we went horizontal again until we found the crawl space and had the ability to dive under the house.
On the back side of the home we came down next to the window and dove under the deck.
Electrical came from the back side of the breaker panel and right into crawl space. We then added a disconnect and flexible whip to the unit.
We set the unit on a styrofoam sound dampering pad.
We added refrigerant charge, registered their 12-year parts and compressor warranty with Mitsubishi and these customer are set to go enjoying the benefits of a nice quiet air conditioning system on those very hot days. As well as heat when next winter comes…